Serviced/tested/repaired at FEI
Starting torque controller
Capacitor bank install
Generator field flashing
Battery load tested 3 banks
Uninterruptable power supply
Charger wiring repair
Auto timer install
DC altimator load testing
Battery box and cell assembly
Battery load tester
Residential wiring repair
Wind turbine output verified
Propane tank adapter built and cut 25 % fill cost.
Solar panel Shipment 3rd party our fleet transfer
Review micro hydro with customer for 80 kw feed mill.
Reveiw micro fit 5 kw on rooftop with paint plus building at 5 point.
Customers backup generator tie in and transfer switch. Gas hook up.
Install 12 ground mount panels.
Good work team.